A case study was done on a piggery in Victory that had been producing electricity since 1991 and it was looking to improve biogas/electricity production from the piggery wastewater stream though it anaerobic reactor.
Piggery was located in Victoria and is owned and operated by the family company since 1970. In 1991 it invested 2 million dollars on an anaerobic cogeneration plant and started producing electricity from the piggery effluent. At present the piggery produces 3000kwh per day of electricity. As the price of electricity has risen and the business has grown a desire to improve production of electricity from the anaerobic cogeneration plant developed.
The anaerobic cogeneration/wastewater plant has seven process steps. (Fig 1)
• Continuous wastewater collection
• Grit removal
• Concentrating wastewater stream
• Anaerobic acidification (primary digester)
• Anaerobic methanogenic (secondary digester)
• Biogas purification
• Power generation
In this system the heat from the generation is used to heat the primary anaerobic system and preheat the effluent wastewater heading into the anaerobic system.
The first step in this field trial was to conduct a simple lab test on different alkali at different strengths.
The lab trial was conducted on four alkaline products hydrated lime, 25% caustic soda, standard magnesium hydroxide slurry and ACTI-Mag Magnesium hydroxide slurry. Each was added to provide equivalent hydroxide levels to the effluent after accounting for the different strengths of each product. (Table 1). A control into which no chemical was added was tested in parallel.
The test procedure involves taking 500 ml of the anaerobic tank material and adding it to 500 ml of the input influent. The alkaline is then added to the 1 litre bottle at the appropriate rate for each product. A balloon was sealed to the top of the bottle to measure the biogas production (fig 2). The 500ml of input effluent was made up of 35% from the DAF and 65% from the solids screen flow. Solids content of the final effluent was around the 3.8% ± 0.5
From the above result it was show that the ACTI-Mag gave the best results at a dose rate of between 100kg to 200kg was the optimum range. From these results the caustic soda didn’t improve the performance in the lab trial at any concentration and in many cases performed worse than the control. A possible reason for this maybe that caustic soda was causing hot spot and killing off the activated slug. The hydrated lime and standard Magnesium hydroxide slurry did not improve the biogas production much above the control (no chemical added).
The first part of the field trial was to get historical data (Graph 1 2014). One of the interesting things in the historical data is the rise in biogas production in the winter period and the lower production in the summer period.
This can be explained by the fact that the pigs in the winter period consume more food to stay warm in the winter and less in the summer.
The ACTI-Mag trial started on the 24th August 2015 and within a small amount of time the biogas production started rising (Graph 1) and the biogas quality, as evidenced by the energy generated per cubic metre of gas, also started rise (Graph 2). When looking a historical data the month of November 2014 and 2015 the biogas production average per day were 1550 m3 and 1860 m3 respectively. With the use of ACTI-Mag the biogas production increased by 20% from one year to the next.
The ACTI-Mag was started being dosing on the 24th August (in Blue)
Looking at November 2014 to 2015 the kwh per m3 production increased from 2.12 to 2.18 respectively. Looking at November 2014 and 2015 (Graph 5) the power generation per day increase from 3286 to 4061 kwh which is a 23.5% increase in overall power generation per day
One of the reasons for the increasing in the biogas production is that the ACTI-Mag chemical promotes hydrolysis or the breaking down of complex carbon molecules into smaller carbon compounds. Fig 3. One of the rate limiting steps in any anaerobic system is the hydrolysis process.
The soluble phosphate level of the incoming and outgoing streams of the anaerobic system was analysed (graph 6). After the application of the ACTI-Mag the phosphate level in the outgoing stream from the anaerobic system reduced from 40 ± 10mg/L to 25 ±5 mg/L whilst the incoming stream level remained unchanged. This indicated that the ACTI-Mag is forming phosphate precipitation.
This system had seen regular blockage in pipes blamed to the formation of struvite. Once the pipes were cleaned and ACTI-Mag dosing begun this problem did not occur during the trial period of 4 months and subsequently has not appeared to April 2016.Thus the use of ACTI-Mag in the system appears to have eliminated the precipitation of Struvite in pipes at the same time as reducing the soluble phosphate level. The mechanism postulated for this is the high surface area and high localised pH on the surfaces of ACTI-Mag particles allows struvite to form on the ACTI-Mag particles and remain in the sludge and not nucleate on the pipes in the system Fig 4. This observation has led to an ongoing research program at both a University and an industrial site.
The H2S levels of the raw biogas were taken before and during the trial (graph 5). The H2S readings were taken on monthly bases with a Dragger gas tube. The application of the ACTI-Mag in August saw a large drop in the H2S level from 800-600ppm range to less than 200ppm.This allowed the operator to remove the caustic soda chemical scrub out of the biogas processing stream ahead of the gas turbine.
Prior to using ACTI-Mag the process used Ferric Chloride and Polymer in the DAF plant for H2S management. The ferric chloride was used in the traditional manner with precipitation of the sulphide into ferric sulphide. The addition of the Ferric Chloride into the DAF reduced the pH which is not favourable for the sulphate precipitation reaction. This is counteracted by the addition of ACTI-Mag which stabilised the pH in the DAF thus enhancing the ferrous sulphide reaction (7). The Ferric Chloride dose is then much more efficient and the H2S levels in the gas are lowered. It also helps in the formation of ferric Hydroxide (Fe(OH)3(s)) which will react with the H2S in the follow reaction (8)
The addition of ACTI-Mag to this wastewater system has also had a financial benefit. Revenue from gas electricity production has been increased and the use of other chemicals has been reduced which easily off-set the cost of the ACTI-Mag addition. The net benefit is approximately $AU 24,363.75 per year
From this case study the application of 125kg of ACTI-Mag per ML to wastewater has led to the following improvements. 1. Biogas volume increased by 20% 2. Power generation increased has increased by 23.5%. 3. The soluble phosphate has been reduced by 37.5% in the final waste stream. 4. The H2S level has reduced from 800- 600 ppm range to below the 200 ppm level. 5. Struvite formation in the pipes and the bell has been eliminated the piggery has achieved a net financial benefit per year of approximately $24,000.00.
Q.Wu, P.L.Bishop, T.C. Keener, J. Stallard and L.Stile. Sludge Digestion enhancement and nutrient removal from anaerobic supernatant by Mg(OH)2 aplication. Department of Civil and Environmental Engineering. University of Cincinnati. OH 45221-0071. USA
Ye Chen, Jay J Cheng, Kurt S Creamer. Inhibition of Anaerobic digestion Process: A review. Department of Biological and Agricultural Engineering. North Carolina State University. Raleigh NC 27695-7625. USA (2007)
Clean Energy Australia Report https://www.cleanenergycouncil.org.au/resources/resources-hub/clean-energy-australia-report
Calix ACTI-Mag can increase the quality and quantity of the biogas coming from anaerobic
systems, and provide a significant economic boost for food processing plants and municipalities.